now browsing by category
Jauregui & Culver provided a design build fueling system for MCAS Miramar including two 30,000 gallon Containment Solutions underground storage tanks, eight Gilbarco dispensers, clean air separator system, and canopy.
Jauregui & Culver, Inc. installed a complete fueling system including an Above-Ground Storage Tank, two Wayne dispensers, two FuelMaster pedestals, veeder-root, and more. Also installed was a complete fueling system for a back-up Generator including Above-Ground Storage Tank, Simplex Packaged Pump Set unit, and piping.
Jauregui & Culver, Inc. removed the three existing diesel above ground storage tanks (ASTs) located at the existing Woodside facility and replaced them with two 12,000 gallon cylindrical ASTs.
Jauregui & Culver, Inc. provided necessary drawings and submittals to the City in order to procure permits. The removal of existing tanks included the removal of the sheet metal roof, sheet metal wall and support framework, and chain-link gates. The existing ASTs were washed and lawfully disposed of. The existing AST masonry support structures, tank slab, curbing, and concrete drive slab were removed so that the new ASTs could be placed side by side with adequate setback distances between the building and the ASTs. The existing diesel below ground piping extending from the pump to the AST enclosure was cut and temporarily capped while Jauregui & Culver, Inc. installed a new SWFG piping transition sump and extended the piping. Jauregui & Culver, Inc. poured a new slab. We furnished and installed 6″ diameter concrete filled steel bollards. The ASTs were assembled and installed.
Jauregui & Culver, Inc. will continue to do the testing and maintenance of this facility, ensuring that it is safe, up to code, and working properly for Dion & Sons.
Jauregui & Culver, Inc. installed an above ground diesel storage tank (AST) for the Wild Animal Park (which is now the San Diego Zoo Safari park.) Jauregui & Culver, Inc. procured permits, poured the slab and put in the tank. We continue to service and provide regulatory compliance testing for the tank.
Jauregui & Culver, Inc. did a full design build for the County of San Diego Operation’s fuel facility. We procured permits, installed tanks, canopy, and a fuel system. We custom built the shoring that went in on the sides of the tank hole. The concrete footings, tank slab, and drive slabs were poured. Jauregui & Culver, Inc. also installed the fuel management system and continues to provide service and testing for the station. The existing fuel site was demolished, and can be seen here.
In addition, Jauregui & Culver, Inc. provided piping for the emergency generator system and is continuing to design build for the emergency generator system and other projects at this facility.
Sam’s Club #4819 Bakersfield was a ground up fuel station. Jauregui & Culver, inc. excavated and installed two 20,000 gallon 87 gasoline and one 20,000 gallon split 12,000/8,000 10′ diameter Xerxes Underground Storage Tanks (UST) and deadmen.
We installed Fiberglass, APT, and steel piping to compile the fueling system, including trenching and gravel backfill. Two 3+1 gas/diesel dispensers and four 3+0 gas dispensers were installed, including the Under Dispenser Containment (UDC) basins, dispenser hanging hardware, and dispenser valance. Brine and vacuum tubing for the Veeder Root continuous monitoring and Pressure and Flow sensors in dispenser for the In Station Diagnostics (ISD). The Healy Clean Air Separator (CAS) was installed as part of the EVR II system.
We provided required Enhanced Leak Detection (ELD) testing of the fuel system at the conclusion of the installation of the fueling system and prior to opening. All fuel lines were purged and the dispensers calibrated, completing this project.
Jauregui & Culver, Inc. procured permits for and installed a 4,000 gallon Above-ground Storage Tank (AST) for diesel and double wall steel fuel piping. We furnished and installed AST remote fill assembly, fuel filtration unit, fuel management control panel, Duplex pump system, and tank monitoring system, including all low voltage electrical wiring and conduit.