now browsing by category
Jauregui & Culver provided a design build fueling system for MCAS Miramar including two 30,000 gallon Containment Solutions underground storage tanks, eight Gilbarco dispensers, clean air separator system, and canopy.
Jauregui & Culver, Inc. furnished and installed the Pryco Remote Fill Station and piped from the remote fill port to the generator’s belly tank with Brugg double wall stainless steel flexible pipe. The piping was run continuous with no joints. We installed a conduit and wiring from the fill station to the generator belly tank to the tank high/low sensor and wired for the solenoid valve. Jauregui & Culver, Inc. provided all testing and inspections.
Jauregui & Culver, Inc. furnished and installed new double wall fiberglass underground piping, fiberglass sumps for the existing tank collar, dispensers and pump containment boxes, and all penetration fittings. All existing product dispenser containment box and tank sumps were removed per DEH requirements and soil samples were analyzed. The existing underground tank, tank collars, and vent lines remained in place.
Jauregui & Culver, Inc. will continue to provide monitoring certification, precision line testing, and SB989 testing to insure the safety and functionality of the site.
Jauregui & Culver, Inc. removed the three existing diesel above ground storage tanks (ASTs) located at the existing Woodside facility and replaced them with two 12,000 gallon cylindrical ASTs.
Jauregui & Culver, Inc. provided necessary drawings and submittals to the City in order to procure permits. The removal of existing tanks included the removal of the sheet metal roof, sheet metal wall and support framework, and chain-link gates. The existing ASTs were washed and lawfully disposed of. The existing AST masonry support structures, tank slab, curbing, and concrete drive slab were removed so that the new ASTs could be placed side by side with adequate setback distances between the building and the ASTs. The existing diesel below ground piping extending from the pump to the AST enclosure was cut and temporarily capped while Jauregui & Culver, Inc. installed a new SWFG piping transition sump and extended the piping. Jauregui & Culver, Inc. poured a new slab. We furnished and installed 6″ diameter concrete filled steel bollards. The ASTs were assembled and installed.
Jauregui & Culver, Inc. will continue to do the testing and maintenance of this facility, ensuring that it is safe, up to code, and working properly for Dion & Sons.
Jauregui & Culver, Inc. provided submittals and drawings of the proposed fuel system necessary for CUPA, Fire Department, and Air Quality agency permitting. We furnished and installed a complete gasoline fuel system that included one 4,000 double wall fiber glass underground storage tank, fuel dispenser, below ground fueling, vapor return and tank vent piping, under dispenser containment, vent transition containment, an enhanced vapor recovery system, and a vapor root monitoring system. This required excavation, disposal of excavated soil, gravel back-fill materials meeting manufacturer specifications, crane, and back-filling operations. The new dispenser was calibrated and brought to compliance and Enhance Leak Detection was provided.
Jauregui & Culver, Inc. installed a complete fuel system which included permits for San Diego County Environmental Health (DEH), San Diego County Air Pollution Control District (APCD) and City of Escondido fire department. a 4,000 gallon double wall fiber glass tank, fuel dispenser, and piping for the below-ground fuel, vapor return, and tank vent. Recovery (EVR) system and a Veeder Root monitoring system were also installed. Calibration for the new dispenser, and regulatory compliance Enhance Leak Detection (ELD) testing were also provided.